Cause 1: The oil fume purifier has too much oil on the electrode plate of the electric field, and there are sundries or electric field deformation in the electric field, resulting in electric field discharge. At this time, the effect of the oil fume purifier is reduced or not.
Solution: remove the electric field for cleaning, remove the electric field to remove impurities or restore the deformed electric field.
The second reason is that the matching of oil fume purifier is too large or too small. The air volume of the equipment is too large to match, and the kitchen oil smoke passes through the equipment too fast. If it passes through the purifier without treatment, the effect will become worse; The air volume of the equipment is too small. Due to the large amount of cooking fume in the kitchen, which exceeds the treatment limit of the equipment, white smoke will appear at the exhaust outlet.
Solution: Refit the oil fume purifier with appropriate air volume.
Cause 3: fan power mismatch. As the auxiliary equipment of the kitchen oil fume purifier, the fan also plays a very important role. Too much fan power will lead to too fast wind speed in the pipeline, and too little fan power will lead to too slow wind speed in the pipeline, which will play a negative role in purification.
Solution: Refit a fan with appropriate power.
Cause 4: There are sundries in the pipeline; If there are sundries in the pipeline, such as the sundries left inside carelessly when installing the pipeline, it will increase the pipeline resistance, affect the pipeline wind speed, and reduce the purification efficiency.
Solution: clean the sundries in the pipeline in time to keep the pipeline clean.
Cause 5: under unreasonable installation, it will cause white smoke in the exhaust. Unreasonable installation, lack of air distribution network at the air inlet and outlet, short pipe spacing, many elbows, and unreasonable diameter change openings will all cause smoke from the smoke exhaust outlet.
Solution: Complete and check the installation work one by one according to the correct matters to prevent the low purification efficiency caused by installation problems.